Views:0 Author:Site Editor Publish Time: 2013-03-27 Origin:Site
1. Frequency terminal selection: 50Hz Operation: Connect terminal C-50; 60Hz Run: Connect terminal C-60.
2, stability terminal selection; 90kW or less: connection terminal A-C; 90KW-550KW; connection terminal B-C; greater than 550 kW; connection terminal A-B.
3. Remote voltage fine tuning terminal: Terminal 1, 2 indirect inlet potentiometers (2K) can perform remote voltage fine-tuning. If you don't have to be used, it will be shorted to use the short-circuit.
More related information consulting our company after-sales service department: 18005264833, 0991-3817210, 0991-3814032