Views: 0 Author: Site Editor Publish Time: 2013-03-31 Origin: Site
Can the generator have not been used for one year, can it be used directly? The answer is definitely can't, then what technical measures do you need to do? My company's technical department gives you a solution
1. Remove all of the cover from the engine, air filter and exhaust pipe
2, if necessary, add the same quality lubricant in the engine, if there is no lubricant filter during the storage process, the new lubricating oil filter is replaced.
3, replace the new fuel filter and clean the fuel system
4, check each drive belt
5, check the state of each hose, check and tighten each hose clamp
6. Turn off the discharge valve and reload all the discharge plugs.
7, check the coolant level. Add it when necessary
8, unfained electric battery on the street
9, startengine. And run to the working temperature before the engine loads
10. Check the leak of lubricant, fuel or coolant
More technical questions consultant Hongjun 0991-3856119, 0991-3817210, 0991-3814032, 0991-3814032, 400-0991036
3KW-3000KW generator set sales phone: 18999222000, 1809953146, 18609915083